Firstly, I am a novice and would have hired someone if I could afford it, but I cannot and have opened up my kitchen walls and am in need of some assistance if anyone can help.
I have a kitchen light with 2 K.T. wires coming in and out, one hot and one not. The light is controlled by a switch at LOCATION 1 via a wire named LINE 1 with a black and white wire attached to a 3-way switch (the white one to the common and black one to one of the others.) There is nothing connected to the other screw. This LINE 1 was added prpbably in the 50's and travels under my floor into a box on the opposite wall in the kitchen. The white from LINE 1 connects to another wire and travels up the wall at LOCATION 2. However, at LOCATION 2, the black wire from LINE 1 meets up and is pig-tailed to a wire (LINE 2) and also pigtailed to a switch at LOCATION 2. It appears LINE 2 is split going up and down in the wall and I believe the upper is the incomeing hot wire. The switch at LOCATION 2 does not appear to control anything and is only a 2-way switch.
I am soooo confused...help!
MICHIGAN MEDICAL MARIJUANA DISPENSARY