How to Replace a Whole-House Plumbing Trap
This Old House plumbing and heating expert Richard Trethewey shows tools and techniques for fixing corroded cast-iron pipe
In this video, This Old House plumbing and heating expert Richard Trethewey shows tools and techniques for fixing corroded cast-iron pipe.
1. Wrap the chain of the soil-pipe cutter around the cast-iron water main, positioning it close to the plumbing trap.
2. Tighten the chain, then ratchet the handle back and forth to cut through the pipe.
3. Break loose the opposite end of the plumbing trap by striking it with a 3-pound sledgehammer. 4. Remove and discard the old trap.
5. Use a ball-peen hammer and cold chisel to chip off the old lead and oakum from the end of the water-main pipe.
6. Use a no-hub coupling to join together an angled cast-iron fitting and a clean-out fitting. Tighten the stainless steel clamps with a torque wrench.
7. Use the soil-pipe cutter to cut a length of cast-iron pipe to fit between the existing water-main pipe and the new clean-out fitting.
8. Join the new pipe section to the existing water main with a no-hub coupling.
9. Set the clean-out fitting into place against the new pipe section.
10. Measure for a new length of pipe to span from the other end of the existing water main to the angled fitting attached to the clean-out fitting. Cut a length of cast-iron pipe to fit.
11. Join the cast-iron pieces together with no-hub couplings.