Just moved into a new house! I just finished installing a 6 slot sub-panel in our attached garage for electric car charging and my table saw and dust collector, etc. My master electrician good friend recently passed and he was the one I ran everything by so I guess y’all get that privilege now :)
100A service homeline
50A breaker in main panel
6ga (2 hot, neutral and 8 ga ground) in 3/4” EMT (1936 house has plastered basement ceiling so I’ve had to do the run under that) 23’ run
40A breaker for level 2 car charger (car will be pulling closer to 29A)
20A GFI X2 for power tools
15A GFI for garage doors
Questions... do I bond the neutral and ground at the sub-panel? I can purchase another bus bar for the box if needed.
Online wire calculators give me max 50A current with 25’ of #6, but I’m Reading people going higher than this on 80 feet? Am I missing something?
Thanks in advance!