I want to install a new ceiling fan and light where there isn't one now. I have a wall switch that controls an outlet. I want to run the new light off of a new switch at the wall and have the fan controlled by the pull chain. The wall switch I want to tie into has 1 black and 1 white wire coming in (no ground). I wired the in the 2 switches and power at all connections in the box but the wall outlet is not woking. I haven't put up the new fan yet until I get the wiring correct. Where am I going wrong?
incoming black pigtailed to the bottom **** connections on each switch
outgoing black to top **** connection of switch closest to door
red to top **** connection on switch away from door
ongoing ground to ground on switch farthest from door
no incoming ground from walloutlet