Step by Step ProjectsTips from the ProsAffordable Remodels
I have a new TIKI HUT next to the pool. I want to run a dedicated 20 amp GFCI circuit to it,for lighting and outlets.The electrical panel is 170 feet from the TIKI HUT.
My question is,is their a distance limitation for GFCI circuit breaker . Thanks
The distance should have no affect on the GFCI but you will have voltage drop issues. I limit using #12 to 150'. Between 150' and 250' I use #10 on a 20amp circuit.
You also need to check with your building department, there are very strict rules and requirements for electricity in a pool area.